Please see below for an overview on glycol chiller sizing with Spike fermenters.
How to use the charts:
- Get the total "Cold Crash" BTU/hr needed for all vessels you want to cold crash at the same time.
- Add the "Maintain Cold Temps" BTU/hr for each vessel that you want to hold at cold temps after the batch is cold crashed.
- Add the "Fermentation" BTU/hr for each additional vessel not counted in steps 1 or 2
- With all of the numbers added together, you now know the minimum amount of BTU/hr needed for your setup. A good rule of thumb is to always allow an additional 20% when picking a chiller.
- 4 CF15 fermenters
- Cold crash 2 at a time = 1400 BTU/hr
- Maintain cold in 1 = 200 BTU/hr
- Ferment in 1 remaining= 100 BTU/hr
Subtotal = 1700 BTU/hr, +20% Buffer of 340 BTU/hr
Total = 2040 BTU/hr needed. 1/3HP Glycol Chiller would be a great fit!
Important Note - The charts assume you are using insulated tanks in mild ambient conditions (<80F) and cold crashing is over an 24hr window. While this would apply to most users there are some who need to make adjustments because their situation is a bit different. Use the numbers for the next size up fermenter if any of the following apply:
•Your fermenting ambient temperature is above 80F
•You would like to fully cold crash in less than 24 hours